NV Energy Cooling System to Cut Water Use by 281m Gallons a Year
The reduction in freshwater use also reduces the facility’s wastewater by the same amount, Nalco said.
The station uses both river and well water in its cooling system, but the source water contains high concentrations of silica, which can cause damaging buildup of sediment in the cooling system. Nalco’s 3D Trasar technology controls the cooling water chemistry with fluorescence-based monitoring and silica dispersant to prevent silica from accumulating, according to the Nalco website.
Nalco said that the deposit occurs when the recirculating water’s silica concentrations exceed 150 ppm and the temperature is less than 70°F (21°C). In NV Energy’s system, silica concentrations were about 230 ppm on average. The incoming water temperature was about 80°F (27°C) with a 20° temperature drop across the tower.
NV Energy also is using 3D Trasar boiler technology at its coal-fired North Valmy Station. The station’s steam turbines were experiencing deposits that reduced overall efficiency. The boiler system controls allow the station to generate the same amount of electricity while reducing fuel consumption by 87,000 tons of coal annually, reducing costs by $3.5 million per year, Nalco said.
Energy Manager News
- Driving Energy Efficiency in Leased Commercial Space is Complicated – and Worthwhile
- Will Co-Firing Natural Gas and Coal Meet Clean Power Plan Standards?
- Pitkin County (CO) Looks for Solar Opportunities
- Solar Panels Working as Promised for Iowa Company
- China and India: Doing the Unimaginable to Address Climate Change
- Maine Solar Bill That Advocates Claim Could Save $100M Is Vetoed by Governor LePage
- Competitive Green Retailer Star Energy Partners Expands to New Jersey, Pennsylvania
- Flying High: Energy Efficiency, Renewables and Airports